|CLASS NUMBER:||4411-01||DESCRIPTION:||OUTLET BOXES AND FITTINGS-Boxes|
Metal and non-metallic boxes not exceeding 100 cu in. in volume* and including enclosures known to the trade as "outlet boxes" and "conduit boxes", armoured-cable boxes, concrete boxes, flexible-nonmetallic-tubing boxes, floor-outlet boxes, flush-device boxes, junction boxes, nonmetallic-sheathed-cable boxes, pull boxes and extension rings or box extenders.
*This does not preclude larger boxes not exceeding the equivalent of the 10-gang in size, each single-gang section of which does not exceed 100 cu in. in volume.
|CSA Standard C22.2 No 0||General Requirements - Canadian Electrical Code, Part II|
|CSA Standard C22.2 No 18||Outlet Boxes, Conduit Boxes, Fittings and Associated Hardware|
|CSA Standard C22.2 No 18.1||Metallic Outlet Boxes|
|CSA Standard C22.2 No 85||Rigid PVC Boxes and Fittings|
The Certified equipment appearing in this classification is judged to comply with the requirements of the NFPA 70 National Electrical Code (NEC).
Note: In accordance with CSA Standard C22.2 No. 18.1, a clamp or other securement means furnished as part of an outlet box shall be marked to indicate the type of application for which it is intended to be used. The following abbreviations marked in lieu of the name of the cable, conduit, and tubing shall apply:
In addition, equipment intended for display, sale or use in the USA is required to include other information such as warning statements, installation instructions, etc., as may be specified in the NEC.
|Copyright © 2013 CSA International. All rights reserved.|